Haas & Sons provides electrical services that includes electrical repair and installations for Elkridge, MD residents and businesses—from lighting fixtures to ceiling fan installation to breaker box replacement and surge protection.
Call us now at: (443) 396-2555 and see why your neighbors rely on us to deliver local electrical services at great value for a fair price in Elkridge, MD below.
for Elkridge, MD
Marc - Elkridge, MD
Alex is an Awesome Guy and Technician! You're in Great Hands!!
Mike - Elkridge, MD
On time answered all questions and explained everything he did and why he did it . Couldn’t be happier with the service. Thanks
Michael - Elkridge, MD
Cut neutrals off neutral bar that were burnt and extremely dangerous. I spliced them to new wires and landed them on different spots on the neutral bar. THIS IS NOT A PERMANENT FIX The neutral bar is comprised and so are many of the breaker terminals We highly recommend installing a new electrical panel ASAP If the customer moves forward with a panel estimate we provided within two weeks of this date may 27th 2021 we will use the 260 dollar bandaid today to the overall cost of the panel job
Removed and replace all devices on circuit which was the devices in both guest bedrooms most of the mast bedroom the hallway light and the hallway bathroom on 2nd floor. Also the kitchen lights I spliced all my appropriate wires together then pig tailed off the splice with one wire then stripped the wire, hooked it around the device screw and clamped it then tightened it down. This is the best possible connection possible. The outlets and switches that were there previously were 30 years old and some had burnt from being back stabbed so customer was loosing power then the power would come back on its own which is dangerous. I also installed two pole breakers where they are required for 14-3 wires in panel and I installed a micro surge protector for the whole home. The 2 pole 15 amp BR arc fault breaker is on back order and we will order that ASAP and once it comes in we will notify the customer so we can come out and install arc fault protection on the circuit I worked on Customer wa
We have replaced the front and lower rear exterior lights with new customer supplied fixtures.
Removed customer bathroom exhaust fan in hallway bathroom. Then replaced it with a company supplied bathroom exhaust fan with 2 speeds and a light I also vented the fan through the room because the old fan was not causing the customers bathroom to start to cause issues with moisture. I also respliced and re deviced all the devices in the bathroom
Customer tried to install a occupancy sensor on powder room light switch. Wiring was not correct so the switches did not function properly. Removed switches and identified hots and switch legs and reinstalled switches and it worked properly. Also fixed a receptacle with a open neutral. Plug on countertop was replaced and the neutral never got hooked up, hooked up the neural and problem was fixed.